By American Society of Heating
The 2008 ASHRAE guide - HVAC platforms and gear discusses a number of structures and the gear (components or assemblies) that contain them, and describes beneficial properties and changes. this knowledge is helping approach designers and operators in determining and utilizing apparatus. it's divided into seven sections:
- Air-Conditioning and Heating platforms
- Air-Handling apparatus and parts
- Heating apparatus and parts
- Cooling gear and parts
- General elements
- Packaged, Unitary and Split-System apparatus
Read Online or Download 2008 ASHRAE Handbook - Heating, Ventilating, and Air-Conditioning Systems and Equipment (I-P Edition) PDF
Similar ventilation & air conditioning books
The 3rd variation of the HVAC Duct building criteria steel and versatile is meant essentially for advertisement and institutional duct development. the traditional comprises tables and info for developing ductwork for ½ to ten wg optimistic and unfavorable pressures. This variation improves upon the second one version with elevated strain category tables, separate tables for TDC/TDF development and extended tables for around duct building together with 6 wg confident and detrimental strain and sizes as much as ninety six.
The publication might be released in a versatile, five" x eight" layout packed with schematic process layouts and snap shots displaying how more often than not measured info can be utilized to spot working issues of the HVAC gear. it truly is anticipated that approximately one region to 1 3rd of the e-book might be line drawing process schematics, pics displaying anticipated information in fault and no-fault states, and some photos of platforms (used simply while this kind of determine is needed for clarifying issues made within the textual content.
The newest radiant ground heating tools and fabrics during this absolutely up-to-date advisor, grasp plumber and long-time contractor R. avoid Woodson explains, step-by-step, tips on how to set up, attempt, and debug in-floor heating systems--the fit, quiet, inexpensive, and fresh heating approach. Radiant flooring Heating, moment variation now bargains information on replacement gas resources and covers new fabric techniques and install approaches, up to date code info, and state of the art piping and heating apparatus.
Those directions deal with the inspection of chimneys and stacks. each one guide assists vendors in choosing what point of inspection is suitable to a specific chimney and offers universal standards in order that all events concerned have a transparent knowing of the scope of the inspection and the top product required.
Additional resources for 2008 ASHRAE Handbook - Heating, Ventilating, and Air-Conditioning Systems and Equipment (I-P Edition)
Indirect evaporation adiabatically cools outside or exhaust air from the conditioned space by spraying water, then passes that cooled air through one side of a heat exchanger. Air to be supplied to the space is cooled by passing through the other side of the heat exchanger. Chapter 40 has further information on this method of cooling. Indirect Evaporative Cooling Fig. 4 Supersaturated Evaporative Cooling Fig. 5 Steam, Hot-Water, and Electric Heating, and Direct and Indirect Gas- and Oil-Fired Heat Exchangers Chapter 6 of the 2005 ASHRAE Handbook—Fundamentals details the psychrometric process of these methods.
Both initial and operating costs affect design decisions. For example, the designer should not arbitrarily design for a 500 fpm face velocity, which has been common for selecting cooling coils and other components. Filter and coil selection at 300 to 400 fpm, with resultant lower pressure loss, could produce a substantial payback on constant-volume systems. Chapter 36 of the 2007 ASHRAE Handbook—HVAC Applications has further information on energy and life-cycle costs. 3 in. of water). It provides a positive return and exhaust from the conditioned area, particularly when mixing dampers allow cooling with outside air in intermediate seasons and winter.
Single Fan With Reheat. There are two major differences between this and a conventional terminal reheat system: (1) reheat is applied at a central point in the fan unit hot deck instead of at individual zones (Figure 11), and (2) only part of the supply air is cooled by the cooling coil (except at peak cooling demand); the rest of the supply is heated by the hot-deck coil during most hours of operation. This uses less heating and cooling energy than the terminal reheat system where all the air is cooled to full cooling capacity for more operating hours, and then all of it is reheated as required to match the space load.
2008 ASHRAE Handbook - Heating, Ventilating, and Air-Conditioning Systems and Equipment (I-P Edition) by American Society of Heating